During the height-of Summer insulation repair, I found that the crawl space was noticeably cooled by leaks of conditioned air, mainly in a very restricted space over the furnace. Where I am not invested in cheap, flawed methods and am known for integrity and professional engineering experience with hydraulics and more, the customer trusted me, to fix the HVAC ducts in the crawl space. I would start over, in a further demonstration of highly efficient ducting that challenges common practice with crudely-hacked D-boxes and octopus ducting.
The story is drawn from this complete photo album:
Furnace Plena And Flex Duct Innovation Multnomah Village October 2014
A sampling of photos and captions is posted to Picasa for public sharing.
Here are some of the photos and captions of the Picasa web album:
A 10” flex duct to a 90° elbow atop the warm-air D-box serves floor registers of the main floor. The elbow lower end is not sealed in any way and loses at least 20% of its flow to the crawl space. It was just too hard to reach. What could the installer do? Simply grab the elbow with a couple of straps, with no tab-ins.
The topside 10” elbow with its two loose straps and a sector of hacked sheet metal concealed but did not seal a badly-nipped D-box opening. No goop here. No tape.
Awful return at bottom. A plate closing the filter box couples with a 16” elbow. Most furnace noise is here. The jet from the 16” elbow has no space to adjust to the shape of the filter. The filter is misaligned with the furnace opening. Velocities far exceed that in developed flow of a 16” duct. More than half of the blower head is simply wasted, right here.
Imagine a better duct system with no D-boxes and with efficient furnace plena, instead.
Use turning vanes and developmen
I believe in turning vanes. Here they are in the air-return plenum. Try to avoid air churning. It does expend energy.
Survey the completed crawl space. An intelligent return plenum with excellent filter, is prettier too.
It is still difficult to view the warm ducts attachment atop the furnace. Now, please be assured, they are leak-free and efficient.
Crawl space headroom is very much improved.
The found crawl space was barely navigable, with octopus supply ducts from a crude hub. All D-boxes are highly resistive to air flow and should be eliminated
In Summer, 2016 This little crawl space portion of a finished basement, was somewhat- "conditioned." Excellent local business Terrafirma Foundation Systems , beautifully and usefully performed Cleanspace Crawl Space Encapsulation .It was well that my work with floor insulation and re-imagining heat ducts, was done first. This extended "furnace room," is still vented to outside, not circulating conditioned air.